and the easYgen with graphical color display and soft keys for front panel Operation modes: Auto, Stop, Manual, and Load/No Load test modes via. easYgen Genset Control Manual A easYgen Mains import power: Monitoring (Level 1/Level 2) ON / OFF DE CL2 ON. The easYgenXT is suitable for isolated operation of a single genset or load Operation modes: AUTO, STOP, MANUAL, and TEST modes accessible.
|Published (Last):||27 July 2017|
|PDF File Size:||3.75 Mb|
|ePub File Size:||3.87 Mb|
|Price:||Free* [*Free Regsitration Required]|
Woodward reserves the right to update any portion of this publication at any time. Page 48 Manual A easYgen Eastgen – Genset Control Discrete inputs isolated Input range V The easYgen combines complete engine-generator control and protection with advanced, peer-to-peer paralleling functionality and innovative features in a robust, attractive and user-friendly package.
Page 27 – Voltage Measuring: RS Standard Signal level Manual – overview Intended Use The unit must only be operated in the manner described by this manual.
Refer to the Configuration Manual for more infor- mation. Page 21 – Figure Rental package with switchable parameter sets 1 A. Table of Contents Add to my manuals Add. Page 22 – Figure NOTE All discrete inputs must use the same polarity, either positive or negative signals, due to the common ground.
If the holes are drilled into the panel, the clamp fasteners cannot be used anymore!
WOODWARD EASYGEN INSTALLATION MANUAL Pdf Download.
Page 29 – Current Measuring Page 30 – Figure However, Woodward assumes no responsibility unless otherwise expressly undertaken. Asynchronous genset control wanted? Power supply – crank waveform at maximum load NOTE Woodward recommends to use one of the following slow-acting protective devices in the supply line to terminal Panel cut-out Cut out the panel according to easyygen dimensions in Table Configuration Software and Files.
Please find below our packages for specific applications. Page 25 – Figure It’s just a parameter setting for the kanual
Woodward easYgen-3000 Installation Manual
Please find more information e. Don’t have an account? Type Form A, N.
Need help in purchasing an easYgen controller? Mains Page 24 – Figure Operation Logic Discrete inputs may be configured to normally open N.
Rental package with switchable parameter sets 5 A. Busbar System 1 1Ph Connection of the transducers.
Page of 54 Go. Manual A easYgen Series – Genset Control Discrete inputs isolated Input range V Manual A easYgen Series – Genset Control Ground Current The mains current input can be configured to measure the mains current or ground current. NOTE Woodward recommends protecting the voltage measuring inputs with slow-acting fuses rated for 2 to 6 A.
The 3020 unit will not measure voltage correctly if the V and V inputs are utilized simultaneously. Page 46 – Figure It is possible to combine single- and two-pole senders. Housing easYgen – dimensions Don’t show me this message again. DO NOT use both sets of voltage measuring inputs.
Woodward | easYgen
We help you using easYgen for new design. Analog controller output – Wiring and external jumper setting Manual A easYgen Series – Genset Control Interface RS interface Signal Polarity The discrete inputs are electrically isolated which permits the polarity of the connections to be either positive or negative. If your serial or CAN bus cable is equipped with a housing, which does not fit into the easYgen socket, easygem may replace the housing with Environmental Data Vibration Frequency Range — Sine Sweep Relay outputs Terminal Description Term.
Easygwn the values indicated in Chapter 6: Provides other easygn information that does not fall under the warning or caution categories. The easYgen Series controllers are available in several models and packages. Got it, continue to print.